Posted in HVAC |
Comments Off on Is this installation legal?
User botlit asks if this photo of an installation is illegal or not? What do you think?
Answer: As long as the vent on the regulator meets the distance requirements to doors, windows, fresh air vents, sources of ignition, etc. it should be legal. Copper can be used as long as it’s flared – or sweated with material that has a melting point above 1,000°F.
Posted in HVAC |
Comments Off on HRV issues/Condensation on ducts.
Stenasasks: I moved into this house in February and it was fairly cold last winter. We’ve had a bit of a cold snap and its been 14 to 30ish for the last week. I went downstairs and noticed a puddle of water on the floor and checked the HRV until above it. There is water dripping down the ducts.
I cleared out the closet and the water is dripping from under the duct insulation (grey wrap tapped at the ends, tape seal was/is loose).
I know this is an issue but is there anything I can do in the interim while I wait for a HVAC contractor to come out?
As an aside: the unit is a Venmar Constructo 1.5ES it hasn’t really worked since I bought the house. If you turn it on its stuck in high mode and you cannot use the singular on unit button to change it to low or panel controlled.
Is the unit not being on adding to the problem?
A: The condensation is caused by the surface dewpoint of the duct being below the dewpoint of the surrounding air. Insulate the duct with a vapour barrier. You could do it yourself. – Deux1
Posted in featured, HVAC, in the news, pr |
Comments Off on RectorSeal® Introduces Safe, Quick and Easy Leak Sealant Injection Method– AC Leak Freeze® PRO
AC Leak Freeze® Pro is the leak sealant formula and applicator combination that’s safe for the HVAC/R service tech and the refrigeration system.
Houston–RectorSeal® LLC, a manufacturer of quality HVAC/R products, has introduced AC Leak Freeze® Pro, a safe, quick and easy refrigerant leak sealant applicator for residential and commercial refrigeration and air conditioning systems.
AC Leak Freeze Pro is an 11.5-inch-long applicator that consists of a flexible, easy-to-handle, transparent refrigeration hose and an attached copper reservoir, which contain a total 1.46-ounces of the same trusted, non-polymer, ac leak sealant formula as the renowned syringe-based AC Leak Freeze injector. Unlike some other disposable leak sealant applicators, AC Leak Freeze Pro doesn’t require a system pump down with R-410A systems and safely withstands all typical refrigerant pressures.
The Pro applicator is designed for use with 1.5 to 6-ton systems and is available with both the blue AC Leak Freeze and green AC Leak Freeze with Magic Frost formulas, the latter which contains a compressor life-extending lubricant additive.
One side of the hose connects to the refrigeration system’s low side. The AC Leak Freeze formula is propelled into the system within seconds once the hose’s reservoir is connected to either the high side or a refrigerant cylinder via a charging manifold. The disposable, one-time-use, AC Leak Freeze Pro applicator’s nylon hose, brass fittings and copper reservoir are all 100-percent recyclable.
AC Leak Freeze Pro is the HVAC/R industry’s safest formula for service technician and the refrigeration system. It’s proven compatibility flows with refrigerant/oil to permanently seal small leaks and prevent them in the future. The patent-pending refrigerant leak sealant formula is not moisture activated, has a safer flashpoint rating than the competition, and doesn’t use polymers that can potentially clog compressors, recovery/evacuation units, Schrader valves, capillary tubes, TXV valves, micro channels or manifold gauges.
Other AC Leak Freeze Pro features are:
hose and reservoir are factory-sealed to prevent injecting air or atmospheric moisture into the system;
the nylon hose’s 45-degree connection fitting allows easier hand access than straight fittings in cramped Schrader valve environments;
transparent hose eliminates guess work as to when application is completed;
and boxed four-color packaging designed for distributor J-hook merchandisers.
Humidity Sensor Operations for Hampton Bay 80 CFM No Cut Ceiling Humidity Sensing Bath Fan
1 Humidity sensing mode. Move the wall on/off switch to the “ON” position. The LED indicator light in the fan is BLUE. The fan will automatically go on when the humidity level in the room goes above 60%.
2 Full speed mode. Cycle the wall on/off switch to the “OFF” position, then back to the “ON” position. The LED indicator light in the fan is AMBER.
3 Fan off. Move the wall on/off switch to the “OFF” position